Country ref. 1083395
StandardsInternational : IEC 60708; IEC 61156
The cable consists of plain, annealed copper conductors with foamed polyethylene (PE) insulation. The cable core is filled with petroleum jelly and wrapped with polyester tape.
The cable is screened with an Al/PE tape. Cables with up to (and including) 50 pairs have a tinned earth wire (7*0.2 mm) under the Al-tape. All cables have an outer sheath of black PE.
Information on electrical data, as well as cable core design and identification, is attached below.
|Type of conductor||Circular, solid|
|Material used for longitudinal water tightness||Jelly|
|Number of pairs||500|
|Nominal outer diameter||56.0mm|
|Minimum breaking load||57kN|
|Maximum pulling force by laying||28kN|
|Maximum tensile load during service (Tl)||1400.0daN|
|Minimum static operating bending radius||405mm|
|Operating temperature, range||-40 .. 60°C|
|Ambient installation temperature, range||-15 .. 40°C|
|Storage temperature, range||-40 .. 70°C|