Country ref. 1088481
StandardsInternational : IEC 60332-1
Declaration of Performance : Reaction to fire: Dca-s2,d2,a2
according to EN50575:2014+A1:2016
The cable consists of plain, annealed copper conductors bundled in twisted pairs. Conductor dimensions are 0.4 and 0.5 mm. Cables with more than 10 pairs have sub-units of 10 pairs, and cables with 200 pairs or more have main units of 50 pairs.
The cable has a longitudinal screen and conductor insulation of halogenfree, flame retardant polymer (PPO). The cable core is wrapped with polyester tape and screened with one layer of aluminium/polyester tape. The cable is unfilled. The outer sheath is a light green halogen-free, flame retardant polymer. The outer sheath is bonded to the screen. Fire performance according to CPR class Dcas2d2a2.
Information on electrical data, as well as cable core design and identification, is attached in the section on Related Information.
|Type of conductor||Circular, solid|
|Insulation||Halogen free thermoplastic material|
|Screen||Aluminium-Polyester tape + tinned copper drain wire|
|Outer sheath||HFFR (polyolefin)|
|Number of pairs||100|
|Nominal outer diameter||19.5mm|
|Minimum breaking load||8kN|
|Maximum pulling force by laying||4kN|
|Maximum tensile load during service (Tl)||200.0daN|
|Minimum static operating bending radius||150mm|
|Operating temperature, range||-40 .. 60°C|
|Ambient installation temperature, range||-15 .. 40°C|
|Storage temperature, range||-40 .. 70°C|